Turbine Acoustic Enclosure
H.S. Engineers design, manufacture sound proof enclosures for gas turbines as well as for other industrial machinery. The noise pollution board norms for Gas turbines is 85 dB (A) at one meter from enclosure surface.
The sound proofs acoustic enclosure does not provide a one-size-fits-all solution, we custom manufacture a sound proof turbine enclosure that fits your space and fits your needs to a tee. The materials, configuration and finish, H.S. Engineers Specialty can custom manufacture a sound proof enclosure that meets your requirements.
H.S. Engineers Specialty can custom configure the Acoustic enclosures, in terms of cutout patterns, doors, louvers, dampers, baffles, mounting options, benches, shelves, sub-panels, rails and just about any special requirement client may have.
H.S. Engineers Specialty’s custom fabricated sound attenuating or acoustical turbine enclosures can also be made to conform to a wide variety as client’s specifications require.
The sound proof enclosure also can manufacture in mild carbon steel, stainless steel (304 and 316), and in aluminum.
Fire & Gas Protection System for Gas Turbine Acoustic Enclosure.
H.S. Engineers design and provide Fire and Gas Protection system for Gas Turbine / Generator Set Acoustic Enclosure.
The Basic Requirements for fire and Gas protection can be Fire & Gas detection & protection system. FGS system with Fire /flame detectors, flammable gas detectors, sounders, visual indicators, inert gas fire extinguishing system and controller. The F&G controller can be installed within IP55 rated FGS panel. This system detect gas occurrence inside the acoustic enclosure and capable of receiving/sending signals from/to the package PLC and central F&G control system in order to protect the unit against fire hazard.
The Gas Engine acoustic enclosure equipped with the following systems-
(i) IR3 type flame detectors.
(ii) IR Flammable gas detectors.
(iii) Inert gas fire extinguishing system.
( iiii ) IR3 type fire detectors
(iv) Shutdown and electrical isolation of the package
( iiv) Shutdown of the ventilation system and closure of its fire dampers.
( iiiv) Initiation of fire suppression system / appropriate alarms (audible and visual) and communication of status / alarm signals hardwired to central fire and gas system
(iiiv) Inert gas fire extinguishing system
All detectors are suitable for installation in a Zone 2 classified area.